Understanding 4 to 20 mA Loops
David A. Snyder, P.E.
This 5 PDH course discusses the uses and limitations of 4 to 20 mA current loops. These types of analog signals are used in almost every domestic industrial facility for analog input and analog output loops. The main limitations of 4 to 20 mA analog output loops are the maximum analog output voltage, the total loop resistance, and the minimum load voltage requirement. The main limitations of 4 to 20 mA analog input loops are the loop power supply voltage, the total loop resistance, and the minimum transmitter voltage requirement. HART communications on 4 to 20 mA analog signals is also discussed. Most of the commonly-encountered process measurements, such as temperature, pressure, level, and flow, are explained with regard to how they are represented by 4 to 20 mA signals. The three major types of modulating control valve characteristics, namely quick-opening, linear, and equal-percentage, are discussed, with detailed explanations of how the 4 to 20 mA signal affects the actuator position and resulting Cv of these valves. There are more than 80 illustrations and dozens of examples to help increase the reader’s understanding of the text. Many examples show how to obtain the answer using two methods – basic math calculations and looking at a simple graph.
This course includes a multiple-choice quiz at the end, which is designed to enhance the understanding of the course materials.
The following learning objectives are included in this course:
Anyone who is involved in the specification, design, installation, or maintenance of 4 to 20 mA loops, instruments, and modulating control valves will benefit from this course.
Benefit for Attendee
Upon successful completion of the course, the reader will have a thorough understanding of 4 to 20 mA analog input loops and analog output loops, including their uses and limitations. The reader will be familiar with the real world parameters and quantities that are represented by a 4 to 20 mA signal.
Most industrial processes have at least one analog measurement or control loop. An analog loop has a signal that can vary anywhere in the range between and including two fixed values, such as 1 to 5 VDC. Other names for analog loops include modulating, throttling, and continuously variable loops. Questions such as “How is differential pressure used to measure flow?” and “What does an analog input current of 10.5 mA mean with regard to the real-world temperature in the process?” will be answered in this course. In addition, the relationship between the load limit graph and maximum resistance formula on transmitter catalog cut-sheets will be illustrated, and examples will be given that will explain how the loop power supply voltage and total loop resistance can be plotted as the operating point on graph of the transmitter’s operating region.
The course content is in a PDF file:
Please click on the above underlined hypertext to view, download or print the document for your study. Because of the file size, we recommend that you first save the file to your computer by right-clicking the mouse and choosing "Save Target As ...", and then open the file in Adobe Acrobat Reader from your computer.
The common-place 4 to 20 mA loop makes it easy to transmit a measured parameter from the instrument in the field to the control system in another location, or to send a control signal from the control system to a modulating control valve or variable speed drive in the field. These 4 to 20 mA signals are useful and simple, but they do have some limitations, as discussed and quantified in this course. In addition, a direct relationship is given between the analog input signal and the measured parameter, such as pressure or temperature, and between the analog output signal and the Cv of the most common types of modulating control valves.
Once you finish studying the above course content, you need to take a quiz to obtain the PDH credits.